Introduce the composition principle of the electrical fire monitoring system, share the design concept and specifications in monitor application. Here introduces the residual current electrical fire monitoring system in super factory, you can know more about function of this system and its advantage.
The Super Factory project has a total of 340pcs ESSL902 residual current fire detectors, installed in plant power distribution room. The L902 residual fire detector is connected to the ESS9000-A electrical fire monitoring host. to the fire control center by Comm-Bus. This system integrates in iron enclosure, wall mount design, convenient for installation, transportation and maintenance.
Electrical fire monitoring system includes three basic components:
Site monitoring host;
Residual current sensor;
Residual current electrical fire monitoring system adopts a hierarchical distributed structure， it’s composed of a station control management layer, network communication layer and field equipment layer.
The electrical fire monitoring detectors are connected to the wall-mounted host through the shielded twisted pair RS485 cable (MODBUS communication protocol).
1) Station control management
This level is aimed at dispatcher consists of monitor software and necessary hardware to provide human-computer interface. Monitoring software can process all kinds of on-site data in real time, and reflect on-site operation conditions to the dispatcher.
Monitoring host: Data collection, processing and data forwarding. Provide data interfaces support for system management, maintenance and analysis.
UPS: Ensure power supply for all system, avoid system disconnect when power off.
2) Network communication layer
System mainly adopts shielded twisted-pair cable, real-time communication between field equipment and host with RS485 interface and MODBUS protocol.
3) Field equipment
The field equipment layer is the data acquisition terminal, mainly use ESSL902-A/B residual electrical fire monitoring detector.
ESSL902 detector designed for TT and TN systems below 0.4kV. It monitors and manages the residual current, wire temperature, overcurrent, overvoltage and other important parameter related fire risk in distribution circuit, to prevent the occurrence of electrical fire.
ESSL902 detector is responsible for the basic data collection, distributed I/O controller connected with the field bus terminal, which can upload the detected data in real-time.